Unfortunately, the item you desire is no longer available in this version. However, we have replaced it with an item with the same functionality. The replacement of this item with a different equivalent item generally takes place at the recommendation of the manufacturer or supplier. Your question and our answer will be publicly visible to all of our customers.
|Published (Last):||2 February 2009|
|PDF File Size:||18.10 Mb|
|ePub File Size:||18.29 Mb|
|Price:||Free* [*Free Regsitration Required]|
If the nPS activation in the did time is reached, switch off and on the instrument to restart normal regulation. Avoid places subject to strong vibrations, corrosive gases, excessive dirt or humidity.
The same recommendations apply to probes. Let air circulate by the cooling holes. Separate the probe cables from the power supply cables, from the outputs and the power connections. Do not exceed the maximum current allowed on each relay, in case of heavier loads use a suitable external relay. It is recommended to place the thermostat probe away from air streams to correctly measure the average room temperature. Place the defrost termination probe among the evaporator fins in the coldest place, where most ice is formed, far from heaters or from the warmest place during defrost, to prevent premature defrost termination.
The alarm stops as soon as the external digital input is disabled again. With the door open, the high and low temperature alarms are disabled. The alarm stops just after the digital input is de-activated. The relay outputs are switched OFF.
The alarm will stop as soon as the digital input is de-activated. The compressor and the regulation are stopped. Program one controller with the front keypad. Turn OFF the instrument. After 10 seconds the instrument will restart working with the new parameters. Check connections before replacing the probe. It starts a defrost if there are the right conditions. To obtain an IP65 protection grade use the front panel rubber gasket mod.
RG-C as shown in figure. Outputs unchanged. Compressor and fans restarts Output unchanged. All outputs OFF. Kind of action: 1B; Pollution grade: normal;Software class: A. Accuracy ambient temp. Necessary cookies are absolutely essential for the website to function properly.
This category only includes cookies that ensures basic functionalities and security features of the website. These cookies do not store any personal information. Any cookies that may not be particularly necessary for the website to function and is used specifically to collect user personal data via analytics, ads, other embedded contents are termed as non-necessary cookies.
Out of these cookies, the cookies that are categorized as necessary are stored on your browser as they are essential for the working of basic functionalities of the website. We also use third-party cookies that help us analyze and understand how you use this website. These cookies will be stored in your browser only with your consent. You also have the option to opt-out of these cookies. But opting out of some of these cookies may have an effect on your browsing experience.
Necessary Always Enabled. Non-necessary Non-necessary.
DIXELL XR60C - mbm-Service GmbH
Quick Links. Download this manual. Digital controller with defrost and fans management. This manual is part of the product and should be kept near the instrument for easy and quick. The instrument shall not be used for purposes different from those described hereunder.
electronic controller DIXELL XR60C-5N3C1 mounting measurements 71x29mm 230V voltage AC NTC
Emerson Dixell XR60C Installing And Operating Instructions
- CHEMISTRY OF NATURAL PRODUCTS BY OP AGARWAL PDF
- BHIMRUPI MAHARUDRA LYRICS IN PDF
- AFI 36 3014 PDF
- LAELIA FURFURACEA PDF
- LIBRO THE LEGEND OF ZELDA 25TH ANNIVERSARY HYRULE HISTORIA PDF
- ANALISIS ESTRUCTURAL HIBBELER DESCARGAR PDF
- ARPEGGIONE SCHUBERT VIOLA PDF
- JESUS CHRIST HEALS CHARLES FILLMORE PDF
- ANTHONY STORR SOLITUDE PDF